In line with customer feedback, Toshiba air conditioning
This would be in addition to the standard power supply obtained from terminal L1 of the interconnecting 3 core & earth cables.
The two separate power supplies required at the indoor unit can potentially give rise to a bi-phasing scenario. This situation can lead to 400v.AC being present across terminal beds (see fig. 1).
We recommend the separate power supply required by the indoor units
The equipment must be installed in compliance with local codes of practice and regulations.
Please refer to page 25 of the installation manual supplied with each indoor unit for further details
Bulletin issued 5th April 2011